Subject: Re: Fwd: FW: CHEM //URGENT: FAULTY AC ROOM COMPRESSOR // REQUEST FOR ATTENDANCE & SUPPLY
From: Operation 2 <[email-masked]>
To: capt sasha <[email-masked]>
Cc: 'operation' <[email-masked]>
Date: Mon, 23 Jan 2023 20:19:42 +0330

Dear captain,

Well noted please advise how long dose it take??

Regards
Mohseni 

On Jan 23, 2023, 8:08 PM, at 8:08 PM, capt sasha <[email-masked]> wrote:
>Dear sir,
>Good evening
>Kindly be informed our technical team inspect the system ,required job
>detail and necessary items for  A/C system fully service  will be as
>bellow:
>1.condeser is chock and to be washed with asid
>2.evapratore and condenser  all tubes to be service,washed with R11 and
>N2
>3.expantion valves and core dryers to be renewed
>4.compressor  has been broken because   capacity of electromotor and
>compressor not mach together thus for avoiding of this problem new
>cylender head with unloader to be install on system
>5.presser test to be carried out and all leakages to be rectified
>6.all system to vacuumed and again charged with gas and made the system
>fully operational
>
>Required material:
>1.N2.      4 bottles
>2.R22.     3bottels
>3.R11.      1bottel
>4.compressor cylinder head with unloader
>5.oil 4GS.      4 drum
>6. Core dryer  2number
>7.wrlding electrodes 13
>8.gage and high press side  sample valve
>
>Price of all above jobs and materials will be 1,900,000,000IRR
>
>*-defected compressor to be shift to work shop and after overhull and
>determind of defected parts price will be announced.
>
>b.rgds
>capt.sasha
>
>
>
>
>در تاریخ شنبه ۲۱ ژانویهٔ ۲۰۲۳،‏ ۱۶:۴۸ capt sasha <
>[email-masked]> نوشت:
>
>>
>>
>> Date: Sat, Jan 21, 2023, 16:40
>> Subject: FW: CHEM //URGENT: FAULTY AC ROOM COMPRESSOR // REQUEST FOR
>> ATTENDANCE & SUPPLY
>> To: capt sasha
>>
>>
>> Dear Captain,
>>
>>
>>
>> As per our telcon Please check below message and  attached file and 
>let
>> us know the result at the earliest.
>>
>> *b.rgds*
>>
>>
>>
>>
>>
>> *Subject:* CHEM //URGENT: FAULTY AC ROOM COMPRESSOR // REQUEST FOR
>> ATTENDANCE & SUPPLY
>> *Importance:* High
>>
>>
>>
>> Dear Agent,
>>
>>
>>
>> Good day to you.
>>
>>
>>
>> As discussed via phone call, we are managing MT Chem which near in
>your
>> premises as of the moment.
>>
>>
>>
>> And we are requesting a help to get quotes for our captioned vessel
>having
>> the *AC Faulty* due to the system require to be  flushed and new
>> compressor with system to make it operational.
>>
>>
>>
>> Additional to this, needs to bring the N2 for -Flushing , Recovery
>plant ,
>> Recovery bottle upon attendance.
>>
>>
>>
>> We also require supply cost for compressor same model as attached.
>>
>>
>>
>>
>>
>> If you will be needing any additional details, please let me know.
>>
>>
>>
>> Hoping your good office could help us out.
>>
>>
>>
>>
>>
>>
>>
>>
>>
>>
>>
>>
>>